I Can’t Get Rid of the Sewer Smell in My Basement?
This is definitely a question we hear fairly frequently and most times it’s relatively easy to troubleshoot. The very first question you should ask yourself or a potential customer is “do you have a floor drain in your basement?”
If there is a floor drain in the basement and it is unfinished it is likely there to receive condensate water from the furnace. Quite often that is the only water that drain ever receives.
So if there is a floor drain and it’s getting very little use the trap serving the drain may have dried out. If this proves to be the case mix a little bit of Mr. Clean or house hold cleaner that gives off a fresh scent with a gallon or so of water. This will do two things, prime the trap and clean out any nasty water that may have been laying stagnant in the trap.
That brings us to the second question and it definitely ties into the first, is there an ejector pit and pump in the basement? If you have a basement and you have an overhead sewer you should have two pits in your basement. One pit with a sump pump to handle ground water and one pit with an ejector and a sealed cover to take care of ANY waste water. Including condensate water.
It is code to have a gas tight sealed lid and the pit should be vented. We should back up for a second. Because most ejector pits only receive condensate waste, home builders frequently put in sump pumps without a sealed lid.
If you have an ejector pit and it is receiving waste water from a laundry, basement bath, kitchen, etc. and it doesn’t have a sealed lid or vent piping there is a strong possibility that pit is the origin. So if you find this is the culprit these are the things you need to fix the problem.
- Purchase an ejector pump
- Purchase an ejector lid with a seal kit. Ejector pits come with two holes; one for the waste discharge and one for the vent. (Try and find a lid that fits your pit. Most times the edge of the pit needs to be modified for the new lid to fit)
- Seal the ejector pit and install the vent piping and tie-in to a vent line overhead.
- Not the Ejector Pump and not a Floor Drain?
So you’ve checked those two things out and there is still a smell in your basement? The next question we would ask is “Are there any plumbing fixtures is the basement?” For example, a laundry room or a basement bath. These groups of fixtures should be vented like any other, we’ve seen plenty of basements vented into the wall and that vent ties into nothing.
The open vent can be the cause if the sewer smell. We have also seen vents for bathrooms and kitchens on the main floors not tied-in, this sewer gas smell can make it’s way to the basement. If the smell can’t be tied to a basement fixture then a peppermint test can be performed.
If it is none of the above you may have a broken sewer line. How would you know or how should someone diagnose the problem? If a sewer line is broken the brackish water is leaching into the ground somewhere. What receives ground water from the area around the foundation? The drain tile system, the water from the drain tile system makes it’s way to the sump pit. That is usually where you will smell the sewer gas.
How to Diagnose the Sewer Line Being Broken.
You have to purchase leak tracing dye. Has anyone here seen pictures of the way the City of Chicago dyes the Chicago River green on St. Patrick’s day? They are using a biodegradable fluorescent tracing dye.
Trace-A-Leak makes dyes in myriad colors. Anyway….the plumbing tech or homeowner should fill up a bathtub and put some of the tablet in the tub or dump some of the tablets in a toilet. Release the water from the tub or begin flushing the toilet. If there is a leak the dyed water will leech its way into the soil and make its way back to the sump pit. This may take some time but it isn’t uncommon.
As always we hope you enjoyed the article and if there is anything our readership would like to add feel free to leave a comment. They are always welcome.